T8400C and T8401C
The T8400C and T8401C Thermostats provide single-
stage, non-programmable temperature control for 24V
heating-cooling systems with manual changeover from
heat to cool. Heating cycle rate is selectable at 1, 3, 4, 5,
When Installing this Product…
Temperature indication can be set for °F or °C.
, or 9 cph. Cooling cycle rate is fixed at 3 cph.
Read these instructions carefully. Failure to follow
them could damage the product or cause a hazard-
Check the ratings given in the instructions and on
the product to make sure the product is suitable for
The T8400C Thermostat is powered through the heating/
cooling system controls. The T8401C Thermostat is
powered directly from the system transformer. Batteries
are not required because setpoints are held permanently
by non-volatile memory for all models.
Installer must be a trained, experienced service
After installation is complete, check out product
operation as provided in these instructions.
All TRADELINE® models include a thermostat, wallplate
(for wiring and mounting thermostat) and owner’s guide.
The T8400C SUPER TRADELINE® model also includes
two decorator cover plates for covering wallmarks.
Electrical Shock or Equipment Damage
Can shock individuals or short equipment
Disconnect power supply before installation.
If this control is replacing a control that contains
mercury in a sealed tube, do not place your old
control in the trash.
Contact your local waste management authority
for instructions regarding recycling and the
proper disposal of an old control containing
mercury in a sealed tube.
Install the thermostat about 5 ft (1.5m) above the floor in
an area with good air circulation at average temperature.
See Fig. 1. Do not install the thermostat where it can be
drafts or dead spots behind doors and in corners.
hot or cold air from ducts.
radiant heat from the sun or appliances.
concealed pipes and chimneys.
unheated (uncooled) areas such as an outside wall
behind the thermostat.
This thermostat is a precision instrument and was
carefully adjusted at the factory. Handle it carefully.
U.S. Registered Trademark
Copyright © 2002 Honeywell •
• All Rights Reserved